What people are saying - Write a review
We haven't found any reviews in the usual places.
Shortcircuitcurrent Calculating Procedures
Symmetrical Components as Applied to Shortcircuitcurrent
Selection of AC Shortcircuit Protective Devices and Circuit
16 other sections not shown
air circuit breakers amperes application approximately arresters autotransformer cable calculations capacitors cent circuit breakers CN CN conductor connected current transformers curves cycle d-c component distribution system equipment example fault current feeder circuit fuses ground ground-fault current high-voltage higher voltage impedance induction motors industrial plants initial insulation interrupter switches interrupting rating kilovars kvar lighting lightning arresters line-to-ground line-to-line load load-center system load-center unit substation low-voltage machine magnitude maximum motor starter motor-starting National Electrical Code neutral normal ohms One-line diagram operating overhead line overvoltages per-unit phase power factor power system primary voltage ratio reactance reactor resistance resistor secondary selective short short-circuit current short-circuit protection short-circuit-current shown in Fig steam supply switchgear symmetrical synchronous motors system voltage Table three-phase time-current trip turbine ungrounded utility voltage drop voltage rating voltage regulation voltage spread volts